Solar Water Heater Sentinel Gold 58 – 300
Solar Water Heater Sentinel Gold 58 – 300
Giá sản phẩm : 9551000
With high heat absorption and long-term insulation mechanism, large-capacity container is the difference of Solar Water Heater Sentinel Gold 58 – 300, helping users save time and costs for direct use of hot water in cooking in their daily activities.
Please contact us for advice:
Son Ha International Corporation
Lot CN1, Tu Liem Industrial Zone, Minh Khai, Bac Tu Liem Dist, Hanoi, Vietnam.
Hotline: 1800 6566
|Step 1||Introduction to the product: Outstanding features, advantages, use, benefits to users||Beyond the limits of the equipment needed in the households, Solar Water Heater is a unique creation with a new perspective in the strategic development of new products of Son Ha.
Proud to be the solar water heater supplier in VN first, SH creates Solar Water Heater with outstanding features such as Power Saving / Environmentally Friendly / Safe for use.
|Step 2||Installation conditions:
Location, flat surface
|The base must be placed on a flat surface without lifting jack. The base plate should be fixed firmly to the exposed flat surface. Depending on the installation location, placing Solar Water Heater toward south or south west angling 10 degrees is the most effective. Distance from the water tank to Solar Water Heater must ensure enough pressure to supply the natural water for Solar Water Heater. In case it is too low or too high, it is necessary to use pressure tank (BNP).
Note: when installing, it is necessary to avoid the location with possible danger such as power wires, tree, or near the wall…
|Step 3||Photos of accompanying tools and installation tools||Prepare enough spare parts, tools for installation in the most convenient place such as wrench, screwdrivers connect screws tightly with the stand bars, Electronic pliers, speculum pliers, water pliers, and welder.|
|Step 4||Photos of BBO containers, vacuum tubes, Solar Water Heater spare part box||To complete the installation of Solar Water Heater water heater should have adequate boxes which contain Insulation bottle, vacuum tubes and spare parts.
Customers can refer to solar water heater installation guide included in the insulation tank.
|Step 5||Insert a vertical bar with the bottle holder||
M6 wrench, screwdrivers 4 edges
|Insert a vertical bar with the bottle holder.
Use a wrench and screwdrivers to tighten bolts.
|Step 6||Insert the cross bar||Insert the cross bar. Use a wrench and screwdrivers to tighten bolts.|
|Step 7||Insert the horizontal bar||Insert the horizontal bar on the right. Use a wrench and screwdrivers to tighten bolts.|
|Step 8||Install the opposite site the same||Insert the horizontal bar on the left. Use a wrench and screwdrivers to tighten bolts.|
|Step 9||Fit the rear brace||Fit the rear brace. Use a wrench and screwdrivers to tighten bolts.|
|Step 10||Insert two rear cross bars||Insert two cross bars toward the south. Use a wrench and screwdrivers to tighten bolts.|
|Step 11||Install tube holder||Install tube holder. Use a wrench and screwdrivers to tighten bolts.|
|Step 12||Install 2 braces for tube holder
(2 small bars)
|Install 2 braces for tube holder. Use a wrench and screwdrivers to tighten bolts.
After completing the installation of the base of Thai Duong Nang water heater, you remember to use screwdrivers and wrench to tighten all bolts before mounting the other parts.
|Step 13||Install the insulation bottle: quickly put the screw to the stand-by hole of the tube holder, balance the BBO before screwing||Wrench M8, screwdrivers 4 edges||Install the insulation bottle: quickly put the screw to the stand-by hole of the tube holder,
Then install two tubes of two heads of the installation bottle, balance the tube with the insulation bottle, then tighten 4 screws in the insulation bottle.
|Step 14||Close the lid (under BBO)||Close the lid under BBO. Use the plier to keep the power-support plug, then rotate in clockwise and push up (in order not to tilt the washer)|
|Step 15||Install vacuum tube: Insert gasket into the tube, connect tube holder with the tube rack, Insert two tubes in 2 sides first||Lubricating solution||Install vacuum tube. First we lubricate the hole. Then insert the gasket into the tube. Note: Insert two tubes in 2 sides first. Align the permanent insulation bottle. Then complete installation of tube.|
|Step 16||Insert the dual thread: Wrap the adhesive tape in the reverse direction of the thread, put it straight to the core.||Adhesive tape, speculum pliers, water pliers||Insert the dual thread: Wrap the adhesive tape in the reverse direction of the thread, put it straight to the core. Then insert the elbow into the insulation bottle. Finally, do the thermal welding.|
|Step 17||Install the discharge valve: Wrap the adhesive tape in the reverse direction of the thread, weld the heat pipe with the elbow and socket. Ventilation tube is 10cm higher than the water supply tank.||Adhesive tape, elbow, socket, heat pipe, heat welding machine, pipe-cutting scissors, speculum pliers, water pliers||Install the discharge valve: Wrap the adhesive tape in the reverse direction of the thread, weld the heat pipe with the elbow and socket. Ventilation tube is 10-20cm higher than the water supply tank.|
|Step 18||Drill a hole on the floor: Position, drill a hold, put the wall plug, screw||Drill, wall plug & screws, wrench||Drill a hole on the floor: Position, drill a hold, put the wall plug, screw|
|Step 19||Complete installation|
|Step 20||Necessary notes: the common mistakes and how to install correctly. Warranty terms, solution for no-sunshine weather, how to choose a good products for some users.||The best time to steam water is 6-7am in order to avoid energy absorbed into the vacuum pipe, breaking the pipe.
When installing, it is necessary to install one input valve and one output valve in order to facilitate repair and warranty.